This chapter defines the corresponding Conformance Units for the OPC UA Information Model for Pumps and Vacuum Pumps.
Table 152 – Conformance Units for OPC UA for Pumps and Vacuum Pumps
|Server||Base System||The PumpType is implemented by the server.|
|Server||Historizing||The Historizing Attribute and the HistoryRead Attribute is True for at least one Quantity.|
|Server||Limit Alarm Status||The ObjectTypes MeasurementsType, DriveMeasurementsType, InletConnectionMeasurementsType and OutletConnectionMeasurementsType have a 0:GeneratesEvent reference targeting one of the subtypes of the 0:LimitAlarmType.|
|Server||PumpClass Data||The PumpClass Property of the Design FunctionalGroup is instantiated for all instantiated Pumps and carries a legal value.|
|Server||Pump Connection Port||At least one of the InletConnectionPortType or the OutletConnectionPortType is implemented by the Server.|
|Server||Pump Control||At least one of ControlType, ActuationType or one of subtypes of ActuationType is implemented by the Server.|
|Server||Pump Drive Port||The DrivePortType is implemented by the server.|
|Server||Pump Identification||Supports the PumpIdentificationType with all its mandatory
InstanceDeclarations, and optionally the optional InstanceDeclarations with read access.
|Server||Pump PumpType Mandatory Nodes||All nodes declared as mandatory in the PumpType are available in the AdressSpace.|
|Server||Supervision Health Status||Every instance of a variable of type 0:TwoStateDiscreteType in the subtypes of SupervisionType has a GeneratesEvent reference targeting one of the subtypes of the 2:DeviceHealthDiagnosticAlarmType.|